Cadet Electric Heater Register Plus Wall Heaters: Cadet RMC202W, Cadet Heater
RMC162W, Cadet Heater RMC151W, Cadet Heater RMC208W, Cadet Heater RM202, Cadet
Heater RM162, Cadet Heater RM151, Cadet Heater RM208, Cadet Heater RM108, Cadet
Heater RM222, Cadet "Register Plus" Electric Heater Accessories
The Register Plus
is Cadet's premier fan forced heater line and is often chosen for its similar
appearance to central system register vents. Models are offered with both fixed
and multi-watt capabilities (multi-watt models factory preset at their maximum
wattage). A large squirrel cage blower quietly provides increased airflow
allowing for lower surface and air-at-surface temperatures. Cadet recommends a
wall-mounted thermostat for optimum performance, or you may prefer the
convenience of an optional field mount thermostat kit.
Fan forced electric air heaters shall be UL Listed, factory rated at
120V, 208V, or dual field rated from 208V to 240V. A 20 gauge wall mounting can
with four knockouts shall be provided with each complete heater. The element and
blower shall be of unitized construction and shall attach to wall can with a
single screw. Elements shall be steel-finned type, with an oversized 25 amp
rating at 240V high temperature manual reset limit switch and an
over-temperature thermal backup. A tangential cylindrical blower delivering
approximately 60 CFM (RM202), and 50 CFM (RM162 and RM151) shall be driven by an
impedance protected motor with permanently lubricated, vibration isolated, dust
sealed bearings. Metal grill shall be of one piece construction and finished
with a powder coat paint system.
A thermostat is
required. For optimum comfort use a Cadet electronic thermostat or a dual
diaphragm thermostat. Fan heaters and thermostats work best when installed on an
inside wall. A double pole, integral thermostat may be installed in the field.
UL requires heater to be placed a minimum distance of 6" (15,2 cm) from adjacent
surfaces and 4.5" (11,4 cm) from the floor. Manufacturer recommends installation
of 12" from all surfaces. A 3' (91.44cm) minimum clearance is recommended for
furniture or other objects placed directly in front of heater.
recommends installing heater assembly after walls are finished. However, if
installation is necessary before walls are finished, use the paint mask
provided. Heater must be cleaned every six months minimum.