Cadet Electric Heater Perfectoe Kickspace Heaters: Cadet Heater UC102B, Cadet Heater UC102W, Cadet Heater UC072B, Cadet Heater UC072W,
Cadet Heater UC101B, Cadet Heater UC101W, Cadet "Perfecto" Accessories
The Perfectoe heater is the ideal solution for areas with limited
wall space. With only 3.5" of height clearance required, this heater can be
placed in under-counter applications such as kitchens or bathrooms.
Stairwells and hearths are also ideal areas for The Perfectoe. Cadet
recommends a wall-mounted thermostat for optimum performance, or you may
prefer the convenience of an optional built-in thermostat.
Fan forced electric air heaters shall be UL Listed, factory rated
at 120V, or dual field rated from 208V to 240V. A 22 gauge housing with two
knockouts and a 45 cubic inch junction box shall be provided as part of each
heater. The heating unit shall be of unitized construction and be secured to
the housing with two screws. Elements shall be of steel-finned type. All
heating units shall include an oversized 25 amp at 240V high temperature
manual reset limit switch and an over temperature thermal backup. A
tangential cylindrical blower delivering 53 CFM is driven by an impedance
protected, permanently lubricated motor. The motor shall be isolated from
the heating chamber. All metal housing components shall be finished with a
powder coat paint system.
A thermostat is required. For optimum comfort use a Cadet
electronic thermostat or a dual diaphragm thermostat. Thermostats work best
when installed on an inside wall. A single pole or double pole integral
thermostat may be installed in the field. UL requires heater to be placed a
minimum distance of 6" from any inside corner or adjacent surfaces.
Manufacturer does not recommend installing heater directly under sink or
where a person may stand for an extended length of time due to discharge of
hot air. A 3' (91.44cm) minimum clearance is recommended for furniture or
other objects placed directly in front of heater. Heater must be cleaned
every six months minimum.