The Economical Choice For Smaller Areas: Cadet CSC202TW, Cadet Heater CSC152TW,
Cadet Heater CSC102TW, Cadet Heater CSC151TW, Cadet Heater CSC101TW, Cadet
Heater CS202, Cadet Heater CS152, Cadet Heater CS122, Cadet Heater CS102, Cadet
Heater CS072, Cadet Heater CS151, Cadet Heater CS101, Cadet Heater CS051, Cadet
Heater CS208, Cadet Heater CS202T, Cadet Heater CS152T, Cadet Heater CS122T,
Cadet Heater CS102T, Cadet Heater CS072T, Cadet Heater CS151T, Cadet Heater
CS101T, Cadet Heater CS208T,Cadet "Com-pak Plus" Accessories
The Com-Pak Plus is our most popular in-wall fan heater. An
economical choice that includes our highly regarded safety components. Offering
models up to 2000 watts at 240V, these heaters are perfect for smaller areas or
larger areas needing the dispersed heat created by multiple heaters. Cadet
recommends a wall-mounted thermostat for optimum performance, or you may prefer
the convenience of an optional built-in thermostat.
Fan forced electric air heaters shall be UL Listed, factory rated at
120V, 208V, and dual field rated from 208V to 240V. A painted 20 gauge wall
mounting can with six knockouts and 34 cubic inch wiring compartment shall be
provided with each complete heater. Each complete heater shall be of unitized
construction and attach to the wall can with a single screw and shall be
self-contained and completely separate from the wall mounting can. Element is of
nichrome type wire wrapped on mica insulators with an oversized 25 amp rating at
240V, high temperature manual reset limit switch and an over-temperature thermal
back-up. A two stage centrifugal blower shall be driven by an impedance
protected motor. The motor shall be totally isolated from the heating chamber.
Metal grill shall be of one piece, 20-gauge construction and finished with a
powder coat paint system.
Order with or without
built-in thermostat. For optimum comfort use a Cadet electronic thermostat or a
dual diaphragm thermostat. Single pole and double pole field mount thermostat
kits available. Fan heaters and thermostats work best when installed on an
inside wall. UL requires heater to be placed a minimum distance of 6" from
adjacent surfaces and 4.5" from the floor. Manufacturer recommends installation
12" from all surfaces. Models without built-in thermostat, 1500 watts or less
may be ceiling mounted. A 3' (91.44cm) minimum clearance is recommended for
furniture or other objects placed directly in front of heater.
recommends installing heater assembly after walls are finished. However, if
installation is necessary before walls are finished, use the paint mask
provided. Heater must be cleaned every six months minimum.