Cadet Electric Heater Com-Pak Max Electric Wall Heaters for Small Area: Cadet Heater CM162, Cadet Heater CM162T, Cadet Heater CM202, Cadet Heater CM202T, Cadet Heater CM208,
Cadet Heater CM208T, Cadet Heater "Com-Pak Max" Electric Wall Heater Accessories
The Com-Pak Max provides all the benefits of our popular Com-Pak Plus, but features more durable components and increased versatility. This multi-watt heater is perfect as a single unit for smaller areas such as a bathroom or small bedroom, or as multiple units for larger areas such as a master bedroom, living room or family room. Choose from a vertical grill with the option of a built-in thermostat, or a horizontal, register style grill without a built-in thermostat, to suit your project needs. Cadet recommends a wall-mounted thermostat for optimum performance.
Fan forced electric air heaters shall be ETL listed, factory dual field rated 208V/240V. The painted wall mounting can for this heater is made from 20-gauge sheet steel with six electrical knockouts and 34 cubic inches for a wiring compartment. Each complete heater shall be of unitized construction and attach to the wall can with a single screw and shall be self-contained and completely separate from the wall mounting can. Element construction is a coiled nichrome heating wire sealed in a steel sheath with steel fins brazed to the sheath. Heating unit shall include a 16-amp rating at 240V, high temperature manual reset limit switch. A two stage centrifugal blower shall be driven by an impedance protected motor. The motor shall be totally isolated from the heating chamber. Metal grills shall be of one piece, constructed of 22-gauge steel and finished with a powder coat paint system.
The wall can and the Com-Pak Max heater assembly may be installed vertically or horizontally. The Com-Pak Plus grill may be installed vertically or horizontally. The Com-Pak Max register style grill may only be installed horizontally. The (vertical installation) Com-Pak Max may be ordered with or without a built-in thermostat. For optimal comfort use a Cadet electronic thermostat. Fan heaters and thermostats work best when installed on an inside wall. UL requires heater to be placed a minimum distance of 6” from adjacent surfaces and 4.5” from the floor. Manufacturer recommends installation 12” from all surfaces. A 3’ minimum clearance is recommended for furniture or other objects placed directly in front of heater. Not approved for ceiling mount.
NOTE: Manufacturer recommends installing heater assembly after walls are finished. Heater must be cleaned every six months minimum. Model CM162 is UL Listed, and models CM202 & CM208 are ETL approved.