Cadet Electric Heater Com-Pak Bath Electric Wall Heaters for Bathroom: Cadet Heater CBC103TW,Cadet Heater CB103T, Cadet Heater CBC132TW, Cadet Heater CB132T, Cadet Heater "Com-Pak Bath" Electric Wall Heater Accessories
The Com-Pak Bath Heater is our most versatile and stylish heater. Equipped with a built-in thermostat and 60-minute timer, it is a great option for adding supplemental heat to any room. The 60-minute auto-timer overrides the thermostat setting for instant warmth and comfort.* The Com-Pak Bath Heater is Cadet’s first heater with both multi-volt and multi-watt options available. Because the Com-Pak Bath Heater fits into any Com-Pak series wall can, it is a great option for replacement, remodel or new construction.
*Once timer expires, control of the heater will return to the thermostat and the previous set point setting.
Fan forced electric air heaters shall be UL listed, factory rated at 120V/240V or dual field rated from 208V to 240V. The painted wall mounting can is made from 20-gauge sheet metal with six electrical knockouts and a 22 cubic inch wiring compartment. Each heating unit shall be of unitized construction and attach to the wall can with a single screw and shall be self contained and completely separate from the wall mounting can. Elements shall be tube and plate, painted, with an over-sized 16 amp rating at 240V high temperature manual reset limit switch. A centrifugal blower shall be driven by an impedance protected motor. The motor shall be totally isolated from the heating element. Metal grill shall be of one piece, 20-gauge construction, and finished with a powder coat paint system.
All heaters include a built-in single pole thermostat and 60-minute timer. The Com-Pak Bath Heater is not to be used with a wall thermostat. The multi-volt option must be configured for the correct voltage before installing the heater. The multi-watt option must be configured for the desired wattage before installing the heater. UL requires heater to be placed a minimum distance of 6” from adjacent surfaces and 4.5” from the floor. Manufacturer recommends installation 12” from all surfaces. A 3’ minimum clearance is recommended for furniture or other objects placed directly in front of heater.
NOTE: Manufacturer recommends installing heater assembly after walls are finished. Heater must be cleaned every six months minimum.